The MTGA 500 series Macro Cell Base Station is a standalone, fully self-supporting unit designed to support a single sector or cell in an LTE system or any other high-powered device in this power range specification.
The 500 series is a base station style (skid style) solution designed to be semi mobile, with crane lifting, dragging and forklift points for transport. The 500 series base station is designed to support approximately 400-600w continuous power draw.
This MTGA solution utilises a patent pending sliding solar array for safety in deployment of the panels as well as quick and easy site establishment. The sliding array means that the base station is compact and eliminates an elaborate set up and pack down process for multiple solar panels.
The 500 series also utilise a backup generator on an as-required basis. It is not needed during typical operations.The base station features a 17m telescopic lattice mast in the standard design (other masts can also be specified and quoted).
The 500 series can either utilise an air-conditioned shelter for the communication equipment and batteries, which maintain all equipment and power supplies below 35 degrees Celsius; or to reduce cost and weight the 500 series can utilise a standalone air-conditioned cabinet for the heat sensitive equipment.
The batteries are housed in an ergonomically designed rack for the shelter design or sliding drawers for the air-conditioned rack design to provide ease of access.
The MTGA 500 Series Macro Cell Base Station is an innovative, intelligent and cost-effective design that meets and exceeds all specifications requested to date.
|Mass:||Approx. 5 – 6 tonnes|
|Type:||Semi-Portable Base Station|
|Power Output (Cont):||400 – 600 Watts|
|Mast Height:||17 metres|
|Mast Type:||Aluminium Lattice|
|Mast Actuation:||Linear Actuator with Electric Cable Winch|
|Supported Headload:||90 kg (at Apex)|
|Supported Wind:||80 km/h @ 1.0 m2 (Un-Guyed)|
|Battery Redundancy:||Up to 5 Days|
|Generator Redundancy:||4 days (120L Tank)|
|Solar Panels:||12 x 360-400 Watt|
|Batteries:||24– 48 x 12V 120Ah or 6V 225Ah Deep Cycle AGM|
|Battery Configuration:||24V / 48V|
|Power Backup:||3.0 kVA 48V/240V Yanmar Generator||Enclosures:||2 x Mild Steel Powder-Coated,
1 x Air-Conditioned 18RU Rack